Click here to book online
or click here to book online
With a combination boiler you don't need any form of water storage tanks at all,
Both the hot water and cold water storage tanks,
As well as the feed and expansion tank for the central heating can be removed.
to your shower or other taps within your property,
then these have to be removed.
One thing that people don't realise is when you have a combination boiler fitted,
it works under high pressure and the boiler that it replaces is normally low pressure.
It may have been OK beforehand working on low pressure,
but it has not been tested working under high pressure.
It doesn't always happen,
but it's something that has to be considered when converting over to a combination boiler.
When converting over to a combination boiler, you have to make sure the incoming water mains pressure is good enough.
I have seen combination boilers that are just about working due to low water pressure.
You need to have at least 1.5 bar incoming water pressure if not more.
They will only boost the incoming water up to 12 litres per Minute, and they are very expensive to buy.
The gas supply needs to be checked when converting over to a combination boiler.
Most boilers these days need a 22 m gas supply and not 15 m as you find on most older style boilers.
they work in a completely different way to the old style boilers.
Condensing boilers suck the gas they need, whereas the old boiler just let the gas in when required.
If you are thinking about converting over to a combination boiler,
If you have more than two bathrooms that will both used at the same time,
then a combination boiler is not really a good idea.
With most combination boilers you can only use one hot tap at a time.
There are some models on the market that will let you use more than one tap,
but they are still very expensive.
With the hot water now working under high pressure you have to check all your hot taps for leakage or dripping,
because before they were working under low pressure.
The same goes for the cold water taps in the bathrooms and toilets.
If you have the cold water storage tank removed and the cold supplies converted to mains pressure,
then again you need to check for leakage on taps for dripping.
Water may be running out of the overflow pipe or continuous running in the pan,
As most ball-valves are fitted with a low pressure valve and will need to be converted to high pressure.
Because with the hot water you are only paying for what you use,
whereas with the old hot water storage tank you paid for a full tank of hot water,
but if you don't use it all, then over time it will start to lose heat and the boiler will then come on to reheat it, costing you money.
If you are considering converting over to a combination boiler then it's a good idea to contact a local gas safe registered engineer or company.
They can advise you on your needs.
You can find your local gas safe engineer on the gas safe register.
Just type in your post code and you will be given three local engineers to make contact with.
If you are interested in converting to a combination boiler,
and would like some more information,
enter your details in the box below and request a callback....
November 16, 2017
Check out my latest articles: EzineArticles.com/expert/Steve_D…
Really personable engineer, good communication before and during job. Prompt arrival and worked very hard... checkatrade.com/DuvalHeating/R…
Reviews of Duval Heating - Central Heating Engineer, Plumber based in Shotley Gate, Suffolk. fb.me/FiIpVDZg
Reviews of Duval Heating - Central Heating Engineer, Plumber based in Shotley Gate, Suffolk. fb.me/9jVxzCWul
November 5, 2017
I liked a @YouTube video youtu.be/qvROvjhrzFU?a Контурирование лица
October 17, 2017
Duval Heating Theme 2017 | Login
Copyright © 1985 - 2017 www.duvalheating.co.uk.
All Rights Reserved.